Possible cause of fault
Automatic night set-back is active
The hydraulic conditions have changed. The pump must adapt to these.
When night set-back is activated
Switch on night set-back using button 3.
In "AutoAdapt" mode
Possible cause of fault: The "AutoAdapt" function is unable to correctly adapt the heating system.
Switch off the pump for 5 minutes using the power switch on the electrical supply line (not the switch on the pump) and then switch back on.
Use button 3 to cycle through the possible curves until "AutoAdapt" has been reactivated. The automatic setting may need up to a few hours to adapt to the system curve.
If this measure does not lead to the desired outcome, the pump can be configured to (specific) curves.
Begin by using button 3 to cycle through the possible proportional and constant pressure curves, testing each setting for approximately two hours.
If there is no increase in the heat supply, please call your specialist technician.